-Appliance module, such as a ZDP100 or similar X10, Z-wave, etc. Device.
Installing the ELK-9200 near the Load1. Turn Off the appropriate electrical circuit at the Electrical Breaker Panel before attempting to install the ELK-9200.2. Mount the 9200 near the Load/Device that is to be controlled. Note: In addition to the Line circuit coming from the Breaker Box to the Load/Device, it will also be necessary to have a nearby 110 VAC for plugging in the appliance style automation module (purchased separately). Virtually any automation appliance module (i.e. UPB, Insteon, ZWave, X10, etc.) can be used with the Elk-9200, as long as it supplies the third (3rd) ground prong.3. Carefully disconnect the Line circuit cable where is goes into the Device being controlled; Water Heater, pump, etc. Re-route this cable into the bottom of the 9200 enclosure using an approved electrical wire clamp (not supplied).4. Connect the two (2) hot wires coming from the Line circuit cable to the terminals marked "LINE" and the neutral wire to the terminal marked "Neutral".5. Run a new section of similarly rated cable from the Device into the top of the 9200 enclosure using an approved electrical wire clamp (not supplied). Connect the two (2) hot wires to the terminals marked "LOAD" and the neutral wire to the terminal marked "Neutral". Reconnect the wires inside the device.REFER TO THE WIRING DIAGRAM BELOW.6. Connect the three (3) prong cord to the automation appliance module and plug it into the local 110 VAC outlet.7. Turn On the electrical circuit and test the 9200 operation by transmitting remote commands to the automation appliance module. The relay/contactor will be noticeable loud when switching On and Off.
Tip: Use a Z-wave appliance module to trigger the relay
Copyright HomeSeer Technologies